Mode d'emploi AEG RTi 102 E Thermostat - Notice page 15
2.4 Function Test
Move the ON/OFF switch to the discharge position
Turn the temperature selector knob until the fan in the storage heater unit switches on.
If the fan does not switch on, the operating and fault indicators on the charging and discharge
control unit must be observed.
2.4.1 Operating and fault indicators on the charging control unit
LED lights „green“ ⇒ no fault
The charging control unit is working perfectly.
LED lights „red“ ⇒ Fault
a) Selector knob for charging (R1) and/or brick sensor (B1) defective
or not connected.
b) Plug-in bridge for reduction of charging factor on the charging
No charging takes place.
LED lights „orange“ ⇒ Fault on the discharge control unit
a) Discharge control unit defective
b) Potentiometer for setting the discharge defective and/or
The room temperature is controlled at approx. 22 °C.
c) Room temperature sensor defective and/or not connected.
No discharging takes place.
These operating and installation instructions are part of the unit and must be kept in a safe place
by the user. In the case of a change of ownership they must be handed over to the new owner.
The specialist must be given access to the operating and installation instructions for any repair
For the Fitter